- 本站编辑:杭州克冷制冷设备有限公司发布日期：2018-06-22 11:08 浏览次数：
During the installation and design of fruit and vegetable cold storage, we should prevent the diffusion of water vapor and air infiltration. The moisture proof and heat insulation layer is set up, so that the cold storage has good sealing performance and moisture proof and steam isolation performance after installation. In the process of cold storage installation and design, the automatic cooling defrosting equipment should be selected for the cold air machine. There should be a reasonable defrosting program and a cold air fan fin temperature sensor to prevent excessive heating.
The location of the cold storage unit is closer to the evaporator, the better it is, and it is easy to maintain and heat dissipation is good. The location of the radiator in the cold storage unit is closer to the cold storage unit. The copper tube of the cold storage unit needs to be insulated through the insulation pipe together with the same direction wires together with the air conditioner. The wires should be protected by corrugated hose or line grooves.